文章來源： 作者：羅茨機電 發布時間：2022-01-12 瀏覽次數：541
Centrifugal fan is one of the ventilation and exhaust equipment widely used in industrial production. It is a driven fluid machinery that depends on the input mechanical energy to increase the gas pressure and discharge the gas. However, affected by knowledge, many business owners often ignore it as soon as it is installed. In fact, the effect of centrifugal fan is different under different states. This paper mainly shares the daily operation and maintenance measures of centrifugal fan, which are explained as follows:
Full voltage starting or step-down electric fan is allowed, but it should be noted that the current during full voltage starting is about 5-7 times of the rated current, and the step-down starting torque is directly proportional to the square of voltage. When the power grid capacity is insufficient, step-down starting shall be adopted.
2. During the commissioning of centrifugal fan, carefully read the product manual and check whether the wiring method is consistent with the wiring diagram; Carefully check whether the working voltage of the power supply to the fan meets the requirements, whether the power supply is out of phase or in the same phase, and whether the capacity of the electrical components meets the requirements.
3、試車時人數不少于兩人，一人控制電源，一人觀察風機運轉情況，發現異?，F象立即停機檢查；首先檢查旋轉方向是否正確；風機開始運轉后，應立 即檢查各相運轉電流是否平衡、電流是否超過額定電流；若有不正?，F象，應停機檢查。運轉五分鐘后，停機檢查風機是否有異?，F象，確認無異?，F象再開機運 轉。
3. During commissioning, the number of people shall not be less than two, one shall control the power supply and one shall observe the operation of the fan. In case of any abnormality, stop the machine for inspection immediately; First, check whether the rotation direction is correct; After the fan starts to operate, immediately check whether the operating current of each phase is balanced and whether the current exceeds the rated current; In case of abnormality, stop the machine for inspection. After five minutes of operation, shut down the fan to check whether there is any abnormality, and then start it for operation after confirming that there is no abnormality.
4. During the commissioning of two speed fan, start the low speed fan first to check whether the rotation direction is correct; When starting the high-speed fan, start it after the fan is stationary to prevent the high-speed reverse rotation from causing switch tripping and motor damage.
5. When the fan reaches the normal speed, measure whether the input current of the fan is normal, and the operating current of the centrifugal fan shall not exceed its rated current. If the operating current exceeds its rated current, check whether the supplied voltage is normal.
The motor power required by the fan refers to the large power required for the centrifugal fan and fan case when the air inlet is fully open under certain working conditions. If the air inlet is fully open for operation, the motor is in danger of damage. During fan commissioning, it is better to close the valve on the inlet or outlet pipe of the fan. After operation, gradually open the valve until it reaches the required working condition, and pay attention to whether the operating current of the fan exceeds the rated current.
The wonderful content of this article is provided by Shaanxi centrifugal fan manufacturer. There are many wonderful content on this website. You can click to enter more content: http://www.makemoore.com We have special customer service to answer your questions