文章來源： 作者：羅茨機電 發布時間：2022-08-11 瀏覽次數：592
Routine maintenance and care of rotary fan:
1. Inspection of lubrication system: the rotary fan shall not run without oil
1. Check whether the lubricating oil in the oil tank is lower than Zui low oil level. If the oil storage is insufficient, please add oil. It is recommended to use 68 # hydraulic oil. In low-temperature and cold areas, the oil grade can be appropriately reduced.
2. Check whether the engine oil is deteriorated due to water and other dirt. If it is deteriorated, please replace the engine oil in time.
3. Clean the oil filter. If it is too dirty, please replace it in time.
4. Check whether the oil dripping condition of the oil drip nozzle is normal. If the oil drip nozzle is dirty, remove the adjusting screw for cleaning.
2. It is very important to keep the environment of the fan room clean and free of oil stain or impurities, and maintain good ventilation.
3. Check the air filter. If it is dirty, remove the air filter, unscrew the butterfly nut, remove the cover, and clean the filter sponge. If it is too dirty, please replace it in time. When removing the filter, be careful not to drop dirt into the fan main body.
4. Check whether there is oil or air leakage in the fan. If so, please repair it in time or contact the manufacturer for professional maintenance.
5. Inspection of the belt: after the fan runs for a period of time, the belt will be loose, elongated or damaged. If it is loose, loosen the fixing bolts of the motor, move the motor, tighten the V-belt to a proper position, and then tighten the fixing bolts of the motor. Note that the end faces of the motor pulley and the fan pulley should be on the same plane. At the same time, check whether the top screws of the two pulleys are loose. If they are loose, please tighten them.
6. Frequently check the flexibility of the safety valve. If it is not flexible, please clean and debug it to ensure reliable opening and closing.
7. Check the operation condition of the fan and motor. In case of abnormal vibration, noise and temperature, stop the machine for maintenance in time to find out the cause of the fault and the corresponding treatment methods.
回轉風機主要用途：一、各種工業污水或廢水處理鼓風曝氣 二、醫院或實驗室、生活污水的污水攪拌曝氣 三、印刷行業的真空送紙 四、塑焊、吹風的氣源供應 六、燃燒器的噴霧、玻璃工業 七、 需要氣源的其他設備
Main uses of rotary fan: 1. Blowing and aeration for various industrial sewage or wastewater treatment; 2. Sewage mixing and aeration for hospitals or laboratories and domestic sewage; 3. Vacuum paper feeding for printing industry; 4. Air supply for plastic welding and blowing; 6. Spray for burners and glass industry; 7. Other equipment requiring air supply
The above is the detailed introduction of Gansu rotary fan manufacturers. I hope it will help you. If you have any questions, please contact us. We will provide services for you with a professional attitude http://www.makemoore.com